|Health and Safety Executive - Safety Alert|
|Department Name:||Field Operations Directorate|
|Bulletin No:||FOD 1-2017|
|Issue Date:||10th January 2017|
Users of Hadar ATEX lighting equipment manufactured by A-Belco Group
This Safety Alert informs end users of potential compliance and safety concerns with certain Hadar Luminaire Products
This alert is aimed at those using the HDL100, HDL106, HDL 206 or HDL109 series of luminaires, part of the Hadar ATEX range of lighting products.
These products were manufactured by the Hadar Division of the A-Belco Group during the period 2006 - 2016 and are intended for use in potentially explosive atmospheres.
Testing of sample products by a Notified Body has identified that they do not meet the required standards for impact resistance and ingress protection or the Essential Health and Safety Requirements of the ATEX Directives (94/9/EC and its replacement 2014/34/EU) based upon the temperature ranges communicated for this range of light fittings. As such they are not considered to comply with the Directive (or the UK implementing Regulations “The Equipment and Protective Systems Intended for Use in Potentially Explosive Atmospheres Regulations 1996” (SI 1996-192)).
Consequently, these luminaires may present a source of ignition that could result in a fire or explosion when used in potentially flammable atmospheres identified under the Dangerous Substances and Explosive Atmospheres Regulations 2002 (DSEAR). They may also fail to operate safely or effectively when used in wet or dirty environments.
Where HDL100, HDL106, HDL206 and HDL109 luminaires are installed in accordance with hazardous zones identified by a DSEAR risk assessment, it is recommended that an inspection in accordance with BS EN 60079-17 is completed. Particular attention should be paid to the following:
It is recommended that any defective luminaires be replaced with products conforming to the requirements of the ATEX Directive and with the required level of protection for the hazardous zone identified under DSEAR. Non-defective luminaires should continue to be regularly inspected and maintained in accordance with BS EN 60079-17 to ensure they are safe for continued use.
For areas not classified as hazardous by a DSEAR risk assessment, where luminaires have been selected as a result of their ingress protection rating and/or provide a safety function, they should be inspected, paying particular attention to points a. and b. above and an assessment made as to whether they are safe for continued use.
The relevant legal requirements are:
Any queries relating to this safety alert should be addressed to:
Health and Safety Executive
Operational Strategy Team
Local Authority and Safety Unit
This alert sheet contains notes on good practice which are not compulsory but which you may find helpful in considering what you need to do.