This document addresses the physical risks and hazards associated with the use of open flame propane fuelled preheating nozzles when used prior to welding to heat a weld preparation, which forms an enclosed space. It may also be relevant if using oxy-acetylene torches.
Although the use of oxy-propane preheating equipment is covered by several sets of legislation, the Management of Health and Safety at Work Regulations 1992 are particularly important. These Regulations require, amongst other things, that the risks from work activities should be assessed in order to determine what health and safety precautions are needed. If there is any doubt about the adequacy of the precautions used, then the risk assessment should be reviewed.
Further advice on welding issues can be found in the welding web pages.
This guidance is aimed at workers and their management / supervision, especially as the risks involved can be reduced by consideration at the design and planning stages.
Before undertaking arc welding, steelwork often has to be preheated to ensure that the weld does not fail because of hydrogen cracking. The methods for achieving this include using an oxy-fuel gas nozzle (ranging from 1H-5H). The preferred sizes of these copper heating nozzles, are known as 3H and 5H. Propane is generally used as the fuel at a consumption rate of about 2 and 4 litres/sec respectively. As an alternative to the 3H and 5H nozzles, fuel gas/entrained air nozzles are used.
There have been several instances of explosion, one resulting in a fatality, where unburned fuel gas has collected inside steel fabricated structures during preheating.
The welding gap can interfere with the flame from a preheating nozzle by allowing the passage of unburned gas through the gap. This can then result in the formation of an explosive atmosphere in any enclosed space behind the welding gap.
For the purposes of this document, an ‘enclosed space’ is that space within a fabrication in which the atmosphere can potentially become explosive as a result of applying a preheating torch to a weld preparation. This document does not advise on work within confined spaces.
The burning of propane (hydrocarbons) is a complicated chemical process in which several different reactions occur at the same time. Part of the process of burning propane is called oxidation and it results in a massive release of energy which is used to heat up the metal. However, if the reaction does not take place with the correct amount of oxygen in the mixture, there will be some unburned gas remaining in the flame.
Weld preparation gaps range from 3-10 mm in width. However, there may be circumstances where larger gaps are found because of distortion and or poor dimensional match between sections to be welded. The typical nozzle to workpiece distance for preheating is about 50 mm, which gives the highest heat input. During the process the torch is moved across the gap to heat up the metal for about 25 mm on either side of the joint. Longer working distances, about 150 mm, are often used during the early stages of preheating to remove surface moisture.
As a lighted nozzle is played over the weld preparation gap, various amounts of unburned gas pass between the plates. Where the weld is intended to seal an enclosed space, then the passage and accumulation of such gas can form an explosive atmosphere within the enclosure. The happens as follows:
Large enclosed spaces, such as the support legs for oil platforms, are just as likely as small ones to contain a flammable atmosphere. Although unburned gas accumulates more quickly during the use of an oxygen-deficient flame, this occurs regardless of flame quality.
The following factors increase the possibility of unburned gas passing through the weld gap:
When a narrow gap is placed in the path of the flame, the mixture entering the gap will be the same as the flame at that point.
The shorter the stand-off distance, the greater the rate of build up of unburned fuel gas behind the weld preparation. Because of the vast amounts of heat available it is possible to have a longer stand-off distance, which still has sufficient energy to adequately preheat the weld. The greater stand-off distance also gives the fuel and oxygen a greater opportunity to mix and reach an ideal balance, ie 'a normally adjusted flame'. Even so, a fuel-rich atmosphere will always be generated in the enclosed space using the open flame process, it will simply take longer to form at greater stand-off distances.
In summary, unburned fuel gas can be expected in all open flame preheating processes that are usually employed with an effective preheat flame length. Operators can greatly affect the rate of build up of unburned fuel in an enclosed space, but it does not appear they can prevent it. Users of open flame preheating process should give detailed consideration to the recommendations contained in this document.
Wherever reasonably practicable, designers and their clients should consider making use of alternative designs of fabrication to those which require the formation, by welding, of an enclosure.
Alternatively, wherever reasonably practicable, other techniques of pre- heating should be substituted in preference to the use of fuel gas. Depending upon the temperature requirements of the preheating these can include radiant preheat gas burners or electrical induction or resistance heaters.
Where this cannot be achieved such as in repair or maintenance, then the following precautions should be adopted.
Operators and supervisors should be properly trained in these precautions and the hazards associated with the use of fuel gas, including how an explosive atmosphere can form after preheating.